From: Zeean Brydon [mailto:[email address]<mailto:[email address]>]
Sent: Monday, 9 May 2016 9:28 p.m.
To: 'Kevin O'Keeffe' <Kevin.O'[email address]<mailto:[email address]>>
Cc: 'Sheryl Barker' <[email address]
Subject: SR356224 - 79 Taranaki Street - Request to confirm Sewer Size
Would you be able to confirm the size of the WW main in Taranaki Road
The 150mm diameter section from WW35573 to WW36428 as shown on Hywel’s long section in the email below.
Zeean Brydon | Associate Engineer
m 022 639 2212
14 Queen St, Blenheim
PO Box 380, Blenheim 7201
From: Sarah Zhou [mailto:[email address]]
Sent: Friday, 6 May 2016 2:16 p.m.
To: [email address]
Subject: FW: SR356224 - 79 Taranaki Street - Capacity Enquiry Response
From: Hywel Lewis
Sent: Friday, 6 May 2016 2:02 p.m.
To: Sarah Zhou
Subject: FW: SR356224 - 79 Taranaki Street - Capacity Enquiry
Hi Sarah, based on 2012 COP the 150mm pipe work downstream of this site is undersized. It would be a good idea to get Kevin to confirm the pipe sizes in this part of the network. Notwithstanding 225mm pipework is also undersized.
Hywel Lewis Senior Engineer Modelling
Tel +64 4 910 3800 DDI [mobile number]
Private Bag 39804, Wellington Mail Centre 5045
Level 4, IBM House, 25 Victoria Street, Petone, Lower Hutt
Wellington Water is owned by the Hutt, Porirua, Upper Hutt and Wellington city councils and Greater Wellington Regional Council.
We manage their drinking water, wastewater and stormwater services.
From: Zeean Brydon [mailto:[email address]]
Sent: Tuesday, 3 May 2016 11:52 a.m.
To: Hywel Lewis
Subject: SR356224 - 79 Taranaki Street - Capacity Enquiry
David Wilson suggested I contacted you about this site – he seems to think you might have a WW model for this area.
I’m looking at this RC for Sheryl Barker, The site is 79 Taranaki Street. The site and existing WW discharge lateral are showing on the attached GIS extract.
The applicant is proposing to convert 5 floors of office to ‘residential’ accommodation.
The current office floor plans show 2 ‘toilet’ areas per floor with a total of 4 urinals, 7 basins, 7 toilets, and 2 cleaners sinks – so not much. Office floor area (including the toilet space) is 841m2 over 6 floors (one floor will remain as office after the conversion) giving a total floor area of 5046m2.
1 floor will remain as office – 841m2.
5 floors will be converted to ‘residential’. This is however high density 1 to 3 bedroom appartments.
Floors 1 – 4 will have 25 beds, 14 bathrooms and 14 kitchen units - I haven’t looked at flows but if you took beds alone this would be equivalent to 8 x 3 bedroom houses.
Floor 5 will have 8 beds, 9 bathrooms and 2 kitchen units – so again based on number of beds – 3 x 3 bedroom houses.
So expecting quite a significant increase in off-site WW discharge.
Is it possible to check if this will cause any capacity issues.
Please feel free to get back to me if you need any further information.
Zeean Brydon. Associate Engineer
Check out our new website
m 022 639 2212
14 Queen St
PO Box 380
Disclaimer to the maximum extent permitted by law, Wellington Water Limited is not liable (including in respect of negligence) for viruses or other defects or for changes made to this email or to any attachments.
Before opening or using attachments, check them for viruses and other defects.
Caution The information contained in this email is privileged and confidential and intended for the addressee only. If you are
not the intended recipient, you are asked to respect that confidentiality and not disclose, copy or make use of its contents.
If received in error you are asked to destroy this email and contact the sender immediately. Your assistance is appreciated.